Dilapidation to Building Reinstatement
Welcome to DMC Group
Dead load brackets were then installed using Fischer FIS V 360s resin and stainless steel A40-70 Threaded rod. Brackets were then installed at designed increments to first floor slab along with helping hand brackets to the second-floor slab. Teflon coated fixings and washers were used on the systems components to reduce friction and provide isolation between dissimilar materials.
Once the installation of the T rails to the brackets had been completed operatives lined and levelled the grid before installing Tenmat Ventilated Fire Barrier at floor slab level. A constant 30mm air gap was maintained between the intumescent strip and the back of the support rail to allow for free air flow with in the compartments.
Once installation of the Fire break had been completed operatives then began installing 110mm Knauf Earthwool Dritherm Cavity Slab to the brick substrate. The insulation was then directly fixed to the building using 6 number plastic tie back fixings with spreader washer and 2 number stainless steel fire rated insulation fixings.
An expansion joint has been installed at every second level to allow for deflection of the internal slab or expansion and contraction of the façade system.
Click to view our Cladding Digital Brochure
DMC House, 7 Bimbury Lane,
Detling, Kent, ME14 3HX
Tel: 01622 631997
Tel: 0151 3191351
Tel: 0161 7379846